On this page you can find answers to frequently asked questions about our products.
If you cannot find a suitable answer to your question here, please send us an e-mail to email@example.com or call our technical service +49 (0) 911 56 93 336 (Mon-Fri 8:00-16:00).
We are happy to help you.
Please contact our technical service at +49 (0) 911 56 93 336 (Mon-Fri 8:00-16:00) or via firstname.lastname@example.org. We will send you the missing manuals by e-mail as soon as possible.
Click here for the follow-up models.
Please check whether the actuator is set to “Manual”. If so, please set it to “Automatic”.
Please connect terminals 1–2.
Please connect terminals L–C
Please connect terminals L–9.
Please check whether the neutral conductor is connected.
The expansion module must be connected externally to voltage.
Please refer to the operating instructions.
This is a warning signal that the radio connection has been interrupted. Please refer to the operating instructions for more information.
Please insert bridge J1.
With this function, INSTAT 868-a4 and -a6 can be used for heating or cooling. The switching behaviour of all outputs is reversed (any activated pump logic is retained without reversal). The timer function is not reversed.
For cooling (summer operation):
1. Press buttons Channel 3 and Reset simultaneously.
2. Release the Reset button first, then the Channel 3 button.
For heating (winter more) = factory setting:
1. Press buttons Channel 4 and Reset simultaneously.
2. Release the Reset button first, then the Channel 4 button.
With this function, the receiver can be used for heating or cooling, e.g. by a central heat pump. The switching behaviour of all outputs is reversed (any activated pump logic and heating control are retained).
Note: The transmitters must not be switched to “Cool”.
For cooling (summer mode): is activated by applying mains voltage to the “Heat/Cool” terminals
When cooling is active, the arrow next to the “sun” symbol is displayed.
Note: There is no temperature increase during cooling. The clock is not used in this case. The temperatures must be adjusted on a master according to the cooling requirements. E.g. T1=21°, T2=24°, T3=27°.
For heating (winter mode): no mains voltage at terminals “Heat/Cool”.